Pipeline type steam water mixing heater is composed of triple-valve body, nozzle, filter plate, discharge plug and filler composition. The water flows in the nozzle at high speed, and it is mixed with the steam emitted from peripheral inclined holes. The required water temperature can be obtained by adjusting the mixing ratio of the two. Metal filler is filled in the nozzle to eliminate noise, its noise is less than 65db.
3 model representation methods
HEG-40——Nozzle throat diameter
Pipeline type steam water mixing heater
4 technical parameter
5 Air conditioning heating cycle system (scanning)
Domestic hot water system (scanning)
6 Installation and use
A. The system will run normally when steam pressure is greater than 0.05MPa B. Pipeline type steam water mixing heater should set an intermediate water tank which is out of showers to prevent the water temperature out of control and then scald people when it is used for domestic hot water system
C. Tthe check valve should be set nearby the steam pipe .
to prevent backflow of water to the steam pipe.